Inline Deflagration Flame Arrester: Eccentric
Inline Deflagration Flame Arrester Eccentric : Explanation
Deflagration = Explosion propagating at subsonic velocity
Inline deflagration flame arresters designed to prevent transmission of a deflagration (explosion propagating at subsonic velocity). Inline deflagration flame arresters are fitted with two pipe connections, one on each side of the flame arrester.
Ignited explosive gas mixture will propagate through the pipe in direction to e.g. storage tank. With pipe length flame speed increases. Up to a certain pipe length / pipe inside diameter ratio, the flame propagates at subsonic speed. Inline flame arrester approved for deflagration stops flame propagation at subsonic speed.
Compared to the concentric design, the eccentric design allows condensate to drain off and allows easy installation in places where the installation is close to the floor or a wall.
Inline deflagration flame arresters has a lower pressure drop than detonation flame arresters.
However, consider when installing inline deflagration flame arrester that the distance from ignition source to inline deflagration flame arrester is limited.
Inline Deflagration Flame Arrester: Short Time Burning
Inline deflagration flame arrester approved for stabilized burning for specified time.For detection of a stabilized flame a PT100 temperature sensor mounted on the unprotected side is necessary! When a stabilized flame is detected an action within 30 seconds has to be carried out which ensures a safe quenching of the flame. (E.g. stopping the gas flow)